Please Note: Adopted standards vary from province to province. Please refer to adopted standards within your province.
Definition of a fault isolation Module CAN/ULC-S536-13
3.21 - FAULT ISOLATION MODULE - A device used in data communication links for wire-to-wire short circuit fault protection.
CAN/ULC -S524-14 Standard for Installation.
10.2.1.44 - Except as noted in Clause 10.2.1.5 data fault isolators, shall be located in a separate enclosure and installed so as to be visible and accessible at all times.
CAN/ULC - S536-13 Standard for inspection and Testing
6.3.1 C - Where power isolation modules are installed in a power distribution riser serving field devices, wiring shall be shorted on the isolated side, annunciation of the fault confirmed, and then a device on the source side shall be operated, and activation confirmed at the control unit or transponder.
E.V.S. SM-001 - Is designed to be permanently installed as a test switch on the isolated side of each isolator serving field devices. Test switches may be conveniently installed anywhere, on isolated side.
Don't forget to label your EVS test switches.