Fixed Temp Heat Non-Restorable
Please Note: Adopted standards vary from province to province. Please refer to adopted standards within your province.
CAN/ULC S536-13 Standard for Inspection and Testing
Definition of inspected
3.33 - INSPECT (inspection/inspected) - A visual examination to determine that the device or system will apparently perform in accordance with its intended function.
184.108.40.206 - Each field device shall be inspected to confirm the following, as applicable:
A Free of damage;
B Free of foreign substance that inhibits the intended operation of the device;
C Mechanically supported independent of wiring;
D Protective dust shields or covers removed; and
E Correctly Installed
220.127.116.11 - Each Non-restorable heat detector shall have the circuits tested by simulating it's electrical operation at the wiring connection.
E.V.S. SM-001 - Is designed to be permanently installed in close proximity to the fixed temp non-restorable heat detector. The E.V.S is directly connected to the heat detector so that a short can be directly introduced via the short on the E.V.S test switch at the wiring connection.
Don't forget to label your EVS test switches.